Add 200g per ton water of this product
into boiler make-up water. During operation, blow-off
every hour, 5-10 second each time. If the boiler has
heavy scale, increase the quantity, and frequently
blow-off. After 10-20 days' continuous operation, stop
the boiler, open the handhole, remove the visible scale
deposit to prevent conduit blockage, then, the boiler
may turn into normal operation again.
would be better if the condense index of boiler water
was controlled within 10. Other parameters may refer to
related regulations (boiler water pH10-12, for example).
pH value should not be lower than 7.
The material of medicate tank should be
in plastic, concrete tank should be pretreated by
anticorrosion method, otherwise, it will be eroded by
the medicine, and the hardness will be increased much
Total hardness of boiler make-up water
should be lower than 200mg/L. Once too high hardness is
countered, lime or other methods should be used to lower
Package and Storage:
200L plastic drum,IBC(1000L),customers’ requirement. Storage in shady room and dry place for one year.
Though no toxic, this product is acidic
and corrosive, once contacted with skin, flush with